Boton very concerns about the safety for our industrial electrostatic precipitator operation. A fire suppression system should be installed in our electrostatic air filters.
The working principle of Boton system：
There are lots of temperature sensors installed at every corner inside the ESP units. If the temperature is too high(over 152℃ ) or flames, the temperature sensor would be broken which would send the fire sign to PLC. Then the fire-fighting procedures will start after receiving the signal as follow:
(1)Alarm rings (2) ESP stops (3) fire dampers shut down for both sides, (4) electrical butterfly valve turn on
All these actions above would be finished within 2 seconds. After 2 seconds, the fire water would come out to put off the fire.